
UPS Systems
 PCs and Servers to 1.5kVA
 Servers and Networks to 3kVA
 Comms Room UPS to 20kVA
 Datacentres 10800kVA
 Rackmount 500VA40kVA
 Modular Systems 25kW1MW
 Models by Size 500VA800kVA
 Models by Technology
 Extended Backup Times
 Single Phase 400VA20kVA
 Three Phase 10800kVA
 Containerised UPS Systems
 120Vac US Systems
 Telecoms UPS
 Industrial Plants
 Marine and Offshore Systems
 UPS with an Energy Saving Eco Mode
 UPS with Super Capacitors
 UPS with Lithiumion Batteries
 UPS with Flywheels
 Generators
 Power Distribution
 Inverters/Chargers
 Battery Systems
 Voltage Management
 Energy Management
 Power/Energy Monitoring
 Renewable/OffGrid Power
 Accessories
 Connectivity/Software

Eco Power Services
 Battery Testing
 Battery Installations
 Generator Services
 Load Bank Testing
 Project Management
 Removals and Recycling
 Remote Site Monitoring
 Repair and Refurbishment
 Site Surveys
 Technical Helpdesk
 UPS/Generator Rentals
 UPS/Generator Relocations
 UPS Installations
 UPS Maintenance Contracts
 UPS Repairs/Spares
 Warranties and Extensions
 Witness Testing
 Eco Power Projects
Electrical and Power Protection Formulas
The information below is provided for guidance only and general project discussions. Measurements and calculations for your specific project must be made by certified engineers. A summary of terms can be found in our website glossary.
 Apparent Power
 Real Power
 Growth Factor
 Power Factor
 Reactive Factor
 Battery Sizing
 Battery Recharge Time
 Solar PV Panel Battery Charging
 Energy Savings
 Energy Efficiency
 Floor Loadings
Apparent Power (VA, kVA or MVA)
Apparent Power is the current drawn by a load at a given supply voltage measured in VA or kVA or MVA. This is the generally accepted formula for UPS and voltage stabiliser sizing when considering ITrelated hardware (nonlinear loads).
Apparent Power (VA) = Supply Voltage (V) x Amps (A)
In the formula (V) is the Root Mean Square (RMS) of the supply voltage. Amps is the current drawn by the load and should be measured at startup and whilst running.
Single Phase Loads: if an electrical device is connected to a 230Vac singlephase supply and the current drawn by this device is 10 Amps, the resulting VA value would be:
10 × 230 = 2300VA or 2.3kVA
Three Phase Loads: a 15kVA three phase UPS supplies 5kVA per phase. To size a threephase UPS the total kVA per phase must first be calculated and then compared to ensure balanced load sharing across the phases. The maximum kVA per phase should then be used to size the overall UPS. For example if the maximum load is 10kVA then the UPS should be sized for 30kVA (3×10kVA).
Real Power (W, kW, MW, GW)
Watts is a unit of measure for the Real Power (also referred to as Active Power) dissipated by a load. This value is generally used to calculate a generator or battery size. Some UPS now use Real Power as their rating as they have a Unity Power Factor and therefore can be considered to draw their power like as a lineartype load.
Real Power (W) = Supply Voltage (V) x Amps (A)
Single Phase Loads: if a linear electrical device is connected to a 230Vac singlephase supply and the current drawn is 10 Amps, then the Watts dissipated will be:
10 × 230 = 2300W or 2.3kW
Three Phase Loads: the maximum kW per phase should be identified and used to calculate the threephase requirements. If this is 10kW maximum per phase, the power protection device should be sized at 30kW (3×10kW).
Growth Factor and Load Headroom
For most applications a typical growth factor for future expansion would be 25%.
Total kVA or kW x 1.25
It is also sound engineering practice to build in headroom of 1020% for reduced component stress and ‘wear and tear’ i.e. run a UPS at 8090% of its rating. So a 100kW generator would have a load of 8090kW maximum.
(Total kVA or kW x 1.25) / 0.8 or 0.9
Power Factor
Power factor is the ratio of real power (W) to apparent power (VA) in an AC circuit and corresponds to the phase angle difference between the voltage and current waveforms drawn. Power factor is calculated as a decimal number or percentage i.e. 0.65pF = 65% between 01pF and 0100% respectively. Power Factor formulae include:
Power Factor (pF) = Real Power (W) ÷ Apparent Power (VA) = CosØ
Therefore, if we know the Power Factor and Real Power we can calculate:
Apparent Power (VA) = Real Power (W) ÷ Power Factor (pF)
If we know the Apparent Power and Power Factor we can calculate:
Real Power (W) = Apparent Power (VA) x Power Factor (pF)
Reactive Power
Reactive power is effectively wasted power and is typically only considered when considering a generator or power factor correction system.
Reactive Power (VAr) = √(Apparent Power² – Real Power²)
Battery Sizing
The battery load can be calculated using the formula:
Battery Load (kW) = (UPS kVA x Power Factor) / UPS Efficiency
The overall load on the battery to take into account the load on the UPS and efficiency losses within the UPS itself. The Battery Load and runtime required (minutes) is used to calculate the overall battery AmpereHour (Ah) size required of the battery string.
UPS and AC Inverters have a Vdc input voltage rating. This DC voltage can be supplied by a single battery or number of battery blocks in a battery string.
Number of batteries per string = Inverter Vdc Bus / Vdc Battery Block
For example a 480Vdc inverter using 12Vdc battery blocks will require one string of 40 batteries. If the battery Ah required is 300Ah and we have a 150Ah Battery Blocks available, the Battery Set will require 2 strings to reach 300Ah.
300Ah Battery Set = 2 × 150Ah Battery Strings
Total number of battery blocks = 2 × 40 = 80
Battery Recharge Time
The recharge curve is nonlinear. A general rule of thumb to an 80% recharge is:
Recharge Time (Hrs) = Battery Ah / Charging Amps
Solar PV Panel Battery Charging
Solar PV panels have a Peak Power Watt (Wp) rating under standard test conditions. For example: 1000W/m² of sunlight (‘peak sun’), 25ºC and air mass of 1.5. Their output varies depending on the amount of solar radiation then receive, module temperature (decreases with temperature) and connected load voltage.
Sunlight data is given in terms of ‘mean daily peak sun hours’ at a given site. For example, daily solar radiation is averaged out to give equivalent number of hours of ‘peak sun’ (or kWh/m²).
For battery charging applications the Peak Current rating should be used as solar PV modules only produce their Peak Power at their Peak Voltage.
Expected Output (Ah) = Current at Peak Output (Amps) x Peak Sun Hours
The Expected Output (Ah) can be multiplied by the battery voltage to give energy output (Wh). Where a solar PV inverter has a wide input voltage range, the Maximum Power Point Tracking (MPPT) will allow the solar PV modules to work at their optimum voltage allowing the following formula to be used:
Expected Output (Wh) = Peak Power (Wp) x Peak Sun Hours (h)
Energy Savings
From Ohms Law we can calculate the Real Power (W, kW, MW, GW) used by a load or total loads within a building:
Power = Supply Voltage (V²) / R
R = Resistance and is a constant factor of a load and associated supply cabling. Electricity is charged for in kWh (KiloWattHours) and so the more the supply voltage is reduced the lower the number of kWh charged for within a given period.
Energy Efficiency
The most commonly used data centre energy efficiency ratio is Power Usage Effectiveness (PUE):
PUE = Total Facility Energy / IT Equipment Energy
Uninterruptible Power Supplies form part of the Total Facility Energy and therefore the higher the UPS efficiency the lower the PUE ratio with 1 being the ideal target number.
GPUE adds a green element to PUE calculations. GPUE includes how much sustainable energy a data centre uses, its carbon footprint per usable kilowatt hour (kWh).
Floor Loadings
Raised Access Floors use pedestals fixed to a concrete base as corner supports for the floor tiles which form the available floor space. The raised access floor will have a specific floor loading which will generally be stated in KN/m². It is important when designing an installation for a raised access floor to ensure that the point loading value is not exceeded. Standard gravity is 9.80665 N/kg and so to convert KN/m² to Metric Tonnes/m² the following formula can be used:
kN/m² X 1Kg/9.80665N = Kg/m²
For a given UPS and battery cabinet we know the footprint (WxDmm) of the cabinet and weight in Kg allowing the floor loading to be checked if required.
For more information please contact us